Peter McCarthy Electric Co., Inc.
Your Cart is Empty
There was an error with PayPalClick here to try again
Thank you for your business!You should be receiving an order confirmation from Paypal shortly.Exit Shopping Cart
Dangerous rooftop exposed wiring
|Posted on December 1, 2014 at 10:27 PM|
Believe it or not, this pipe (first 2 pics from top) that had been beaten up and pulled far apart was still live. Those wires between the two pulled apart section of pipe were very live when we got up there. Amazing.
The pipe we ran was set off the surface of the roof and attached to wooden blocks that are eventually painted to retard water seepage and then glued down to the roof. I learned a long time ago NEVER EVER shoot a screw into a sealed flat roof. This piping was to provide power for an additional down-spout de-icing cable that needs a dedicated GFCI circuit.
Also, you can't see it here, but whenever I run conduit outside like this I always pule and additional grounding conductor for a redundant grounding safety measure. The Chicago and National Electrical Code don't require it in this situation; the metallic pipe itself provides the ground. But I have seen too many situations where the pipe has rusted away or been banged apart or subject to some type of physical damage, which separates the two pieces, breaks the metallic continuity and therefore compromises the integrity of the grounding. It is only a small additional investment to pull a dedicated grounding conductor along with the power wires you are pulling anyway. I think all electricians should do this.
Categories: Do it Right the First time, will ya?
- General (54)
- Emergency service calls (3)
- Cloth-covered wire (8)
- Do it Right the First time, will ya? (15)
- Total rewires (4)
- Electrical Fires waiting to happen! (5)
- Paperwork, Office and dealing with clients (1)
- Customer reviews (18)
- Electrical Fires (1)
- All about Lighting.... (6)
- Big Jobs (5)
- KItchens (1)
- "If it ain't broke, don't fix it!" (In other words, wait for it to start a fire or (1)
- New Services (1)
- New 200 Amp Services (1)
- Gorgeous lighting (2)